Model # 009847
Model # 009847
Availability Please allow 3 - 4 weeks for delivery - Please allow 3 - 4 weeks for delivery
Digital control with liquid crystal display (LCD) for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement.
We are putting in a salt water pool that is 22000 gallons, would it be better to get polymer or cast iron headers, and would 266k BTU's be adequate?
Hello Dan - Both the polymer and cast iron headers are designed for salt water. The cast iron headers are only required for commercial applications. For salt water. we would recommend a heater with a cupro-nickel heat exchanger. We would recommend the Hayward 300,000 BTU. This heater would require a high elevation kit if you are above 2,000'.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.