Part # 009192
Warranty 1 year
Manufacturer Code PR206AMN
Alternate Part #'s 009192
PLEASE NOTE: THIS IS A STOCK PHOTO. THE MILLIVOLT HEATER DOES NOT HAVE A DIGITAL DISPLAY/READOUT.
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
What is the warrantee period on this item
Please click here to view the Ray Pak warranty policy.
how far does the pool heater have to be from the house - huntington ny
For U.S. installations, the point from where the flue products exit the heater must be a minimum of 4 ft below, 4 ft horizontally from, or 1 ft above any door, window or gravity inlet into any building. The top surface of the heater shall be at least 3 ft above any forced air inlet, or intake ducts located within 10 ft horizontally
How many years could I expect this heater to last Raypac 206AMN nat gas
Good morning Loren, There is not really a set life expectancy. If the heater is installed right meaning there is a bypass for plumbing and you cover it when not in use. You will prolong the life. It's like anything else in life. If you take care of it. It will take care of you.
Heater giving a sensor fail reading, does it need replacement or can fault be cleared?
Hi Patrick, You do not have to replace the entire heater, the unit can be fixed. The Raypak Owners/Instructions Manual has a few troubleshoot step that you can follow to diagnose where the problem lies.
I bought a new heater and when it is on it makes a whistling noise. is this common or is there a problem?
There's a problem and you need to get a hold of RayPak so they can get you the correct replacement part for that. Their number is 805-278-5300.
what tube is the inlet coming from the inlet, left or right side
Hi Jim, the water inlet and outlet ports are on the right-hand side of the Raypak heater.
We have a small jacuzzi/pool size 12x8 and we have natural gas. How many BTU do we need to heat it up to 97F? Thank you for your prompt response.
Hi Alicia, I would estimate that this heater would give you a raise of roughly 8 degrees per hour on pool / spa of your size.
do you have a customer service number or direct land line Also what would be the shipping time for a raypak 206000 btu to cleveland
Hi Dennis, Our Customer Service line is 877.372.6038. This unit ships via truck which can take 5-7 business days.
What does the code SNS mean?
The error code SNS on a Raypak heater means the temperature sensor is out of acceptable range. We recently posted an article on the Various Raypak Error Codes and the Possible solutions for the SNS error based on this article are: 1. Water temperature is below 36F or above 110F. If the two thermistors are more than 2 degrees apart, the SNS code will appear. 3. Loose or corroded connection at P1. 4. If the sensor is not mounted all the way into the JACO fitting on the header, it may give a false reading.
just bought a new heater to replace old 1. need a stack adapter only. forgot to take off old heater. heater is inside a pump house . can you sell me 1 ? Part # 011461F
Hi, We do ot currently have p/n 011461F listed on the site but it can be added if you're still in need of this part. Please reply if you are.
WHO CAN SERVICE YOUR POOL HEATER.
Any certified installer is qualified to install a heater to by able to get the warranty.
Gas is on &I here spark heater did not light
Hi Ron, According to the Raypak Owners/Instructions Manual you will need to "Check gas supply, gas line size, gas pressure. Also check for insects or debris in pilot output."
I am replacing a teledyne laars model epg125 125,000 input natural gas millivolt it is below the hot tub and everything is inside. will this heater work? also do I need to do anything with the gas valve and does it need a pressure control.
Bob- You can use this heater, but you will need to call your gas company to make sure that your gas line can supply the 206,000 BTU's that this heater requires and as well as verify that you have the right sized tubing to handle that change in gas. If this is for indoor installation you will also need to make sure it has sufficient ventilation. The indoor installation will require an indoor stack kit. You can refer to the owner's manual for gas line specifications and requirements as well by clicking here.
What is the tube size o.d. and i.d. of the heating element.
Edwardo, That information can be found via the RP Series Technical Data Sheet.
We want to replace our Tele. Laars model Mark 4 325, natural gas pool/spa heater Pool size-32' X 16'; 3' - 9' deep with a built in spa. A 1" gas line; 55' to gas meter with 5) 90 degree bends. Which heater do you recommend?
Hi Dennis, We would suggest the 206,000 Raypak heater here on this page as it is the largest BTU heater that can handle a 1" line at 55'. Also we really like the Raypak line as they have been very high quality heaters for us.
Hi, I have a Pentair 200000 natural gas heater. The gas pipe going into the heater is 3/4" could I go with the 266000 heater? Thanks Best regards
You would be able to go with the 266,000 BTU heater as long as the run of gas line between the heater and gas valve did not exceed 15'.
how do you wire this furnace, what will i need, i can do basic wiring, replacing another heater with electricity there.
Paul, The Raypack Pool Heater model 009192 is a millivolt heater. The advantage of using millivolt ignition is that no electrical power needs to be supplied to the heater. The heater can therefore be located in areas where no electrical service is readily at hand, or where it would be prohibitively expensive to provide electric service.
Will this heater work on an above ground pool with 22,000 gallons of water?
Yes this would be a good choice for a 22,000 gallon above ground pool, you would just need to get with your gas company to see what size gas line you would need to run.
what size heater do I need for an in ground pool size 36x18 from 3 feet to 8 feet
I have a 26000 gallon inground pool what heater do you recommend and I have natural gas
We would recommend the 336,000 BTU heater. The milivolt version would be model 009194.
Can I buy heater with the water inlet on the left side?
The heaters are all shipped with the water inlet/outlet on the right side. The inlet/outlet can easily be switched to the left side once you receive the heater.
I have a tight space I am attempting to fit a heater into, what are the dimensions of the heater cabinet?
For the Raypak 206 BTU RP2100 Series the cabinet measures are as follows:Width - 20 inches, Depth - 28inches, Height - 38 inches.Any fuirther techinical data be found in the Raypak Specifications Guide
Is it possible to convert this heater from natural gas to propane?
This heater can be converted to propane as there is a conversion kit for it. The part or model number for the conversion kit to convert this heater to propane is: 6234-70.
Is there an elevation requirement for the 009192 / PR206AMNC #50 heater?
Yes. This heater is only rated for use betweent 0 - 2000 feet.
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.
What are the dimmensions of this heater?
This heater is 20 inches wide X 28 inches deep and 40 inches tall.
(5 out of 5 stars)
Reviewed By: Dave R. from Mason City, IA ()
Pros: Reasonable price; good quality
Cons: Switching header outlets
The Raypak 206000 BTU heater was relatively simple to install and after a plumber put the gas line in she was up and running. Heated my pool from about 60 deg up to 78 deg. which is where I usually keep it. I would recommend it to others . My pool is 24000 gallon vinyl lined. Had to swirch the header to the left side and that was somewhat time consuming but worked well.