Part # 009200
Part # 009200
Warranty 1 year
Manufacturer Code PR206AMP
Alternate Part #'s 009200
PLEASE NOTE: THIS IS A STOCK PHOTO. THE MILLIVOLT HEATER DOES NOT HAVE A DIGITAL DISPLAY/READOUT.
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
I have a Raypak 206A Natural gas and would like to convert it to LP is there a kit and or individual parts I can purchase to make the switch? I know defiantly orifices but am unclear if the gas valve needs replacing. Thanks
Hi, Roger. If you have the MilliVolt (MV) unit, the NG to LP Conversion Kit is Part # 004690B. If you have the Electronic (IID) unit, you will have to replace the entire Burner Tray Assembly which is Part # 010411F. If you can provide the complete model # of your unit I can confirm what you'll need.
how far does the pool heater have to be from the house - huntington ny
For U.S. installations, the point from where the flue products exit the heater must be a minimum of 4 ft below, 4 ft horizontally from, or 1 ft above any door, window or gravity inlet into any building. The top surface of the heater shall be at least 3 ft above any forced air inlet, or intake ducts located within 10 ft horizontally
what size of s pool heater would I need for a 25' round above ground pool, my last heater was a Pentair, and it seemed to take a long time to heat up the water in pool, would like something that would have a quicker response. what would you suggest?
Hello. I will provide you with a few suggestions you can research. Hayward A/G Pool Heater 100000 BTU NG ELE MODEL# H100ID1 at page ww.inyopools.com/Products/02200459000638.htm?Keywords=h100id1 Next would be for the Propane option Hayward A/G Pool Heater 100000 BTU LP MODEL# H100IDP1 at page http://www.inyopools.com/Products/02200458000639.htm?Keywords=h100idp1 I would also recommend using a solar blanket so you do not loose heat during times of evaporation. Please review the 28' Round Clear Pool Solar Blanket MODEL# NS488 at Page http://www.inyopools.com/Products/00100001005484.htm You would need to cut the blanket to fit 3-4" less than the actual size of your pool. In your case, the pool is 25' round and we do not offer one that size.
I have a confined space I am attempting to fit a heater into, what are the dimensions of the heater cabinet?
For the Raypak 206 BTU RP2100 Series the cabinet measures are as follows:Width - 20 inches, Depth - 28 inches, Height - 38 inches. Any fuirther techinical data be found in the Raypak Specifications Guide
Can this heater be converted from propane to natural gas?
This heater can be converted from propane to natural gas as there is a conversion kit to do so. The part or model number for the conversion to natural gas is: 6234-300.
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.
What are the dimmensions of this heater?
This heater is 20 inches wide X 28 inches deep and 40 inches tall.