Part # 009195
Part # 009195
Warranty 1 year
Manufacturer Code PR406AMN
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
Please Note: The Natural Gas Heaters with Millivolt Ignition are not available in California.
Is the gas lie located on the left side?
Hi, Rich. Yes, the gas line is located on the left of the unit looking at the unit's control panel.
can plumbing enter from left or right side?
Hi, Don. The heat exchanger assy can be rotated from the left to right. This process will have to be done by a professional.
Which one would I purchase for a salt water 40x16. Approx 25k gallons.
Hi, Sean. I would recommend the Raypak Heater 406,000 BTU's NG ELE W/ Cupro-Nickel Heat Exchanger - 014941.
What size or how many BTU would a 50 k gallons would require?
Hi, Ricardo. Heaters are sized based on the surface area of the pool. You can use our The BTU Size of your Swimming Pool Heater Chart to determine what size heater you'll need once you've calculated the surface area of your pool.
how far does the pool heater have to be from the house - huntington ny
For U.S. installations, the point from where the flue products exit the heater must be a minimum of 4 ft below, 4 ft horizontally from, or 1 ft above any door, window or gravity inlet into any building. The top surface of the heater shall be at least 3 ft above any forced air inlet, or intake ducts located within 10 ft horizontally
What size Raypac natural gas heater do I need for a 30,000 gallon pool
I would suggest a 406,000 BTU heater for a 30,000 gallon pool you just want to make sure you have the proper gas line size. The 406,000 uses a minimum of 1" natural gas line and this would be if your run of pipe is 20 feet or less. If your run of gas pipe is 21' - 95' you would require 1 1/4" pipe and if your run is between 96' and 215' you would require 1 1/2" gas pipe.
What gas connection size is required for proper installation of this heater?
The RayPak RP Series requires a .75 inch gas connection.
The this heater be converted from natural gas to propane?
This heater can be converted from natural gas to propane. In order to convert this heater to propane you will need a conversion kit. The part or model number for the conversion kit to convert this heater to propane is: 6234-70A.
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.
What size natural gas line should be used on a Raypak 406,000 BTU heater?
The 406,000 uses a minimum of 1" natural gas line and this would be if your run of pipe is 20 feet or less. If your run of gas pipe is 21' - 95' you would require 1 1/4" pipe and if your run is between 96' and 215' you would require 1 1/2" gas pipe.