Calculate Shipping Charges
Ask a Question
| View Answers (5)
item is in stock
truck line delivery
includes free shipping
Back To Top
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
Please Note: The Natural Gas Heaters with Millivolt Ignition are not available in California.
RP Series Technical Data (175.56 KB)
RayPak Gas Heater Warranty (22.05 KB)
RayPak Heater Brochure (590.64 KB)
Please feel free to view our complete library of owners manuals.
What gas connection size is required for proper installation of this heater?
The RayPak RP Series requires a .75 inch gas connection.
The this heater be converted from natural gas to propane?
This heater can be converted from natural gas to propane. In order to convert this heater to propane you will need a conversion kit. The part or model number for the conversion kit to convert this heater to propane is: 6234-70A.
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.
What size natural gas line should be used on a Raypak 406,000 BTU heater?
The 406,000 uses a minimum of 1" natural gas line and this would be if your run of pipe is 20 feet or less. If your run of gas pipe is 21' - 95' you would require 1 1/4" pipe and if your run is between 96' and 215' you would require 1 1/2" gas pipe.
Replacement parts for Raypak RP2100 R185A-R405A Heaters (11/01/93-11/01/98)
Be the first to review this product.
Write A Review