Part # 009203
Part # 009203
Warranty 1 year
Manufacturer Code PR406AMP
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
how far does the pool heater have to be from the house - huntington ny
For U.S. installations, the point from where the flue products exit the heater must be a minimum of 4 ft below, 4 ft horizontally from, or 1 ft above any door, window or gravity inlet into any building. The top surface of the heater shall be at least 3 ft above any forced air inlet, or intake ducts located within 10 ft horizontally
How do I calculate the size of heater needed ? Pool is 11 x 4 x 1.5 metres, in sub-tropical location... thanks
If you are trying to heat the pool only and you do not have a hot tub to heat I recommend a heat pump over a heater. It is going to be more cost efficient.
Can you provide me the dimensions for the Raypak RP Series model PR406AEP? What size gas line does this heater use?
The Raypak 406 BTU RP2100 Series the cabinet measures are as follows: Width - 29 inches, Depth - 28 inches, Height - 38 inches. the gas line needed for the 406K BTU is a 3/4 inch. Any further technical data like voltage be found in the Raypak Specifications Guide
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.