CAM SETTING TABLE - This table is used to determine the cam settings for any of the four actuator mountings. As you can see the cam settings are based on both the actuator mounting and the direction of water flow. For example, for Mounting A, if the water enters port 2 (the center port and flows out ports 2 and 3 (the end ports) both the lower cam and the upper cam will be set 12 o'clock. This is the common, standard setting used in most installations. In another example for Mounting A, if the water enters port 3 and exits ports 1 and 2, you would have to set the lower cam at 3 o'clock and the upper cam at 6 o'clock. Note: all clock settings are referenced from the small slot on the shaft. See the picture in the next step. One other note. This table shows the setting for valves used to DISCHARGE water (after the pump). For valves on the suction side of the pump (before the pump), the table is the same except the headings in columns 2 and 4 would be switched. Column 2 would read "PORT WHERE WATER EXITS", and Column 4 would read "PORT WHERE WATER ENTERS".