Part # 009193
Warranty 1 year
Manufacturer Code PR266AMN
Alternate Part #'s 009193
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
Please Note: The Natural Gas Heaters with Millivolt Ignition are not available in California.
Where can I find an instruction manual for a 2006 raypak millivolt n/g 266,00 BTU pool heater? How to I restart the pilot light?
Hi, Sandy. Click this link >Raypak Owners/Instructions Manual< to download the manual for your unit.
how far does the pool heater have to be from the house - huntington ny
For U.S. installations, the point from where the flue products exit the heater must be a minimum of 4 ft below, 4 ft horizontally from, or 1 ft above any door, window or gravity inlet into any building. The top surface of the heater shall be at least 3 ft above any forced air inlet, or intake ducts located within 10 ft horizontally
Can this heater be converted from natural gas to propane?
Yes you would need this Raypak Conversion Kit.
would this be suitable for a 30 thousand gallon pool
Hello, This would be a suitable unit, but I would recommend the electric unit versus MV.
How soon would this be shipped? What would be the estimated time of arrival to Minnesota? 55033 Thanks
Mark, Heaters are typically shipped within 24-48 hours after your order has been placed (not including weekends). Delivery usually takes 5-8 business days. Please note that this is a 266k btu, natural gas, millivolt heater.
can we reverse the water manifold to the opposite side. (from the right side to the left side) thank you Roger
Hi Roger, The water connection can be reversed in the field. The reversal and installation has to be done by a pool professional or an authorized Raypak installer or else the warranty will be voided.
I just purchased a Raypak Millivolt heater from you to replace my old Millivolt heater. I have a separate Jandy control system to turn on/off the heater for pool and spa modes. I don't see a wiring diagram for the Millivolt in the O&M manual as to how a Jandy system would be inter-connected. Can you point me in the right direction?
Hi Eric, MV units can not be controlled or wired to an external controller
my pilot light on my raypak 266000 will not stay lit. Any suggestions would be appreciated
Bob, In The RayPak MV Owners Manual on page 43, there's a few things that can cause the issue you're having. They've also provided some solutions that you can try to see if that will fix your issue.
Estimated delivery time on heater
Estimated delivery on this heater would be 3-5 business days.
Is there a conversion kit to convert this heater from natural gas to propane?
Yes, there is a conversion kit to convert this heater from natural gas to propane. The part or model number for this kit is: 6234-70.
Is the Raypak PR226AMN a cupro-nickel heater?
The Raypak 009193 (PR266AMN) is not a cupro-nickel heater. The cupro-nickel is only available in the digital model which is a Raypak 010103 (PR2266AENX): http://www.inyopools.com/Products/04000013058201.htm
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.
(5 out of 5 stars) Warms the water quickly
Reviewed By: Fred64 from sterling heights, MI ()
Pros: Old Ray Pak lasted over 16 years (many hard winters)
Nicer than my 16 year old RayPak that needed to be replaced. This one has no rust headers and fewer items than need attention when winterizing. INYO had the best price for my pool heater. Delivery was quick without hassles. This milivolt model works great with no electrical lines required.