Part # 009194
Part # 009194
Warranty 1 year
Manufacturer Code PR336AMN
Dimensions 38" H x 26" W x 28" D
Alternate Part #'s 009194
PLEASE NOTE: THIS IS A STOCK PHOTO. THE MILLIVOLT HEATER DOES NOT HAVE A DIGITAL DISPLAY/READOUT.
Dial control for temperature selection and heater settings
Capron resin headers prevent rust stains from harming pool surface
Plumb directly from provided 2" PVC threaded union
Smart microprocessor controls diagnostic read-out and continuously monitors operating status
Completely field serviceable
Guaranteed high wind reliability
Looks smart and works smart
1 Year Warranty
Thermal Efficiency of 83%
California Customers Please Note: South Coast Air Quality Management District ( SCAQMD) Area of Jurisdiction REQUIRES a Low Nox Heater be installed. The following 6 California Counties are affected: Los Angeles, San Bernardino, Ventura, Orange, Riverside, & Kern. Installing a non-compliant heater in these counties will void the manufacturer's warranty and could result in a fine from your local code enforcement. Click here for RayPak Low Nox Heaters
Elevation: 0 Ft. – 2000 Ft. Click Here for High Altitude Pool Heaters
We currently have a RayPaK 266000 btu ng heater. It lasted 10 Years, any value to upgrading to a 336000+ heater? The pool is 18 x 38 and averages 6 ft deep. We are in wisconsin.
The larger the unit the faster the pool will heat.Since the unit is larger and able to heat faster it will turn off quicker. As far as up sizing you would have to review the gas line sizes you currently and see if they will match the specs to the 366k.
Does this unit have electronic ignition?
Hi, Skip. This specific unit is not equipped with an electronic ignition system. The Raypak Heater 336000 BTU NG ELE - PR336AEN / 009218 is the model with the electronic ignition system.
how far does the pool heater have to be from the house - huntington ny
For U.S. installations, the point from where the flue products exit the heater must be a minimum of 4 ft below, 4 ft horizontally from, or 1 ft above any door, window or gravity inlet into any building. The top surface of the heater shall be at least 3 ft above any forced air inlet, or intake ducts located within 10 ft horizontally
What is the gas line size for the 266,000 btu and 336,000 BTU?
For the 266,000 BTU it is 3/4" for gas line runs up to 15', 1" for up to 50' and 1.25" up to 210'. For the 336,000 BTU it is 3/4" for gas line runs up to 10', 1" for up to 30' and 1.25" up to 140'
Since this is a millivolt heater, why is it necessary to attach electric?
Hi, Mike. Milivolt unit does not require electricity.
There are 2 wires hanging out of the side in picture 2 what are they for?
Hi, The wires are for the electrical connections.
What are the 2 wires for?
This Heater has quite a few wires. You will need to be a little more specific in order for us to answer your question. You can also reference the Raypak RP2100 R185A-R405A Heaters parts diagram for additional help.
I have a Raypak 336 heater. Can I use it for salt water pool/
To know for sure, we would need to know the full model number of your specific heater. This heater is a standard copper heater exchanger which is not compatible with saltwater pools. Only heaters with Cupro-nickel heat exchangers are suitable for saltwater. Check your heater's model number if it ends with a "C" it is copper, if it is an "X" then it is Cupro-nickel. For example, PR366AENC or PR336AENX
I am replacing a Raypak RP 2100 Digital. Do I need to be concerned about the old gas and water connections not working on the Raypak PR336AMN?
Hi Vernon, The gas and water connection would be the same on current unit verses the older units.
What is the weight of RayPak 336 BTU 009226? And can the shipper deliver it to a house without a loading dock ?
Hello Michael, weight of the unit 300 pounds. This unit includes free shipping and lift gate.
What are the 3 dimensions? HxWxD It needs to fit in a small pool house with plumbing outles to the viewers right as one faces the heater ; ie the heaters left.
Hi David, the dimensions on the Raypak 336,000 BTU heater is 38" H x 26" W x 28" D
How loud is the heater?
Hi Bob, I don't have a decibel rating on this Raypak heater but it is very quiet. I have a similar heater on my pool and you can barely tell when it is on.
What are the dimensions of this heater? What heater do you suggest for a 30,000 gal inground pool and hot tub?
Do you carry the vent piece on top of heater to vent from heater to roof of a small wooden shed?
Hello, For the 009194, you will need this indoor stack kit.
The this heater be converted from natural gas to propane?
This heater can be converted from natural gas to propane. In order to convert this heater to propane you will need a conversion kit. The part or model number for the conversion kit to convert this heater to propane is: 6234-70A.
What is the difference between an Electronic and Millivolt ignition?
The basic answer is that Millivolt is the old style of ignition, using a standing pilot light. While the electronic ignition uses a spark start system like a gas grill. Electronic ignitions are more efficient in gas usage and also are better suited for high wind areas where a pilot light might get extinguished.
Will a gas heater operate at the low speed of a dual speed motor?
Probably not - Most gas heater will shut off at low GPM levels (20-40) to keep the heater cores from overheating - 20 for 200 BTUs, 40 for 400 BTUs. Depending on your pool system you might get these GPM levels at the low speed but generally these heaters must be run at the motor's high speed.