The Compupool Salt Chlorine Generator is a high-performance salt water chlorination system that lets you enjoy perfectly clear pool water without the use of harsh chemicals. It is a safe, clean, easy alternative to dosing your pool with dangerous and expensive chemicals. The Compupool Salt Chlorine Generator is setup and automatically controlled by its Compupool Control Unit. This guide shows you how to operate and read the touch pad controls and LED lights on the Compupool Control Unit.
ON/OFF – This button turns power to the Control Unit on and off. In an OFF state, all LEDs are off and the display will show the current time and POWER OFF. To turn the Control Unit ON, press the button once. The POWER ON LED and one of the POLARITY 1 or 2 LEDs will illuminate and the display will show time and the % of current Chlorine Output setting. Note that this button only turns on power to the Control Unit. The SET TIMER and OUTPUT functions (described next) may have to be set to pass power to the Cell and generate chlorine.
SET TIMER – The Control Unit has the option of working off an external timer or off of two internal timers. This function allows you to set two internal timers to generate two chlorination cycles per day. To enter the timer mode, press the SELECT button and hold it for 3 seconds. The Display screen will ask WHAT LANGUAGE? Select a language with the up and down arrows. Then press SELECT again. The Display will now show WHICH TIMER? EXTERNAL. If you want to bypass the internal timers, press SELECT to go to the next setting (SET CLOCK). If you want to set the internal timers, press the down arrow to change the setting to INTERNAL. Pressing the SELECT button again will display ON TIME 1. Select the start time hours for Timer 1 with the up/down arrows. To change AM to PM, you have to keep scrolling through the hours until you get to the AM or PM setting you need. To set the minutes, use the right OUTPUT arrow to move the cursor from under the hours to under the minutes and then change minutes with the up/down arrows. Press the SELECT button to display OFF TIME 1 – set the end time for Timer 1. Set TIME 2 using the same process as above. Then press SELECT once more to SET CLOCK. A final push on SELECT will exit and return your Display to normal operation mode.
SET CHLORINE OUTPUT LEVEL –The Chlorine production level can be set from 0% to 100 % in increments of 10%. To set the production level, press the OUTPUT arrows left or right. The % Output level will be shown in the Display. Note, at a Output level of 0% the Cell is turned off and the display will read OUTPUT OFF.
SUPERCHLOR - There are occasions when you will need higher than normal amounts of chlorine to be generated - when you have an abnormally high swimmer load, after a heavy rain, or if you have a cloudy water condition. To increase the level of chlorination, simply press the SUPERCHLOR button. This electronically "super chlorinates" the water by increasing output to 100% for a cumulative 24 hours. If, for example, your pump runs 8 hours a day, the Cell will remain in SUPERCHLOR mode for three days before returning to normal operation. Or, if you elect to stop SUPERCHLOR at any time, you can simply push the SUPERCHLOR button again to return to normal operation.
WINTER MODE - If you are not using your pool during the winter months, we recommend that you put the chlorinator in WINTER MODE by pressing the WINTER MODE botton. This reduces the output of chlorine by 50% of your current output setting. For example, if your output is set at 80%, pressing the WINTER MODE button will reduce the output to 40%. To return to normal operation in the spring, push the WINTER MODE button again.
OVER SALT LED - When illuminated, indicates that the salt level is too high. To get the salt level back to acceptable levels and turn off this LED, purge some water out the WASTE line of your filter and add fresh water to the pool. See our guide on "How To Reduce the Salt Level In Your Pool". If you do not bring the salt level to within the acceptable, the cell will draw more current, run hotter, and fail.sooner than normal.